Size - 140 / 120 / 75 mm.
Weight - 1, 0 Kg.
Outside protection surface - IP 54.
Really out alarm level and rely out for second alarm
level. The contact of relays are same switching group
- ( SPDT ) 5A/ 250V - ÀÑ .
In front of:
Three red lights , signaling of gas.
Green light - normal work.
Time hold group
provide temperature stabilizing at initial transformer
"Fogaro" by initial switch-on or blocked from electricity
shock. In that time the light is off. In that way is
provide for right functionality at control equipment.
For example : Without reason doesn't have to switch
-on the break -down light , alarm signal and light signal
, fans and other equipment provide safety.
-orange light - there is electricity.
-button of clearing - by gas , light red is on and system
memorize status. The red light is continue on and after
restoring of initial condition. The memory is clear
off by button "Clear".
The module Main automatic controlling force switch -off
or own fender. With error the system give a break-down
signal to break-down board as gas alarm level 1 /A1/
The assembly of "Main" is making at outside control
zone in room with normal safe region perfectly to see
and control the place.
Size: - 89 / 89 / 58 mm.
Weight - 0 , 250 Kg.
Outside protection surface - IP 65.
Class of safety (Ex) ia IIC T5.
The sensor /initial transformer/ is type 813 "Figaro"
with average exploitation limit of 9 years is catalytic
and change his internal resistance in range of 10 to
1 KO, depending on gas and concentration. The sensor
processing analog signal from detector and when the
signal reach level work the out give signals to "Main"
for first warning level /A1/ and if there is more gas
the detector signaling for second alarm level /A2/ -
over normal gas environment. The signal is potential
Gas sensors are assembled in explication zone, where
it can be gas in place with distance from floor near
to 0.25- 0.35 M. Recommended is to be safe from vibration
and mechanical damage, fluids a.s.
Undesirability is there is gas with other mixture./litter
or other / there is warning of damage of initial transformer